[an error occurred while processing this directive]
Posted by george on January 16, 2004 at 03:53:43:
In Reply to: Re: oil control relay posted by Harold hydronicnetwork.net on January 15, 2004 at 08:00:37:
In checking why the relay is not closing when
the thermostat is calling for heat. Can I
assume that the thermostat shorts the "T"T"
terminals? If so I plan to short the terminals
and see if the relay closes...
Also where does the "F"F" terminals go to? I
assume that "F"F" has something to do with the
aquastat for the domestic supply...
Post a Followup