[an error occurred while processing this directive]
Posted by Matt Leech on December 30, 2003 at 08:10:15:
In Reply to: Re: Ferroli Modena 80E posted by Gavin Yuill on December 13, 2003 at 10:21:09:
I have a Modena 102e and had the same problem as described in the first post on this thread, i.e. the boiler kept switching off and on every few minutes, in fact sometimes it would only stay on for five seconds or so.
Anyway, I read Gavin's comment about the temperature sensors with interest and decided to buy and replace them myself.
The job took about an hour which included draining and refilling the central heating system.
The switches were £10+VAT each which when compared to the quote I got over the phone for an engineer to come and confirm the problem and then fix it of £150!!... it's a bargain.
For all those people who need a manual, I've scanned mine and put it up on my website:
I realise that this is for the 102 version, not the 80 version, but they're very similar. Hope you find this helpful.
Post a Followup