[an error occurred while processing this directive]
Posted by Gavin Yuill on December 13, 2003 at 10:21:09:
In Reply to: Re: Ferroli Modena 80E posted by mark on December 11, 2003 at 02:08:39:
I have fixed mine now - both thermistors were broken - replacing both has brought the boiler back to life. Check the thermistors with a multimeter, they should give a reading of about 8k ohms at room temp. I paid 8 pounds for each thermistor from a local spares supplier.
Feel free to email me if you need any advice.
: same problem aswell!!!!!!!!
: sometimes my house is warm, sometimes its cold. dunno wot to do, or how to fix it!
: has anyone had any success in fixing the problem?????
Post a Followup