[an error occurred while processing this directive]
Posted by jtown on December 22, 2003 at 07:13:32:
In Reply to: Air Scoop/Schraeder Valve posted by KBT on December 22, 2003 at 06:43:07:
You may still have dissolved gases from refilling with fresh water or have a leak that is causing more to come in. Valve off the make up line once you are at pressure to eliminate that cause. The schraeder should be on top of a float operated vent. Air will build slowly to get enough to operate the float so there will usually be a little bit there. If you are closing the vent's cap tight it will not release the air. When refilling the system you should run it a couple of hours to get gases out.
Post a Followup