[an error occurred while processing this directive]
Posted by george on February 05, 2005 at 07:10:00:
In Reply to: Re: cold radiators and hammering posted by Dave Wasserman on February 04, 2005 at 13:41:12:
Just put a bucket under the purge
valve, with the furnace not
running and lower the level
to no less than 1/2 the site
glass. There is a lot of histerisis
in the water movement. The water
filler should cut in if you moved the
level too low.
How often do you purge the sediment
from the boiler?
Post a Followup