[an error occurred while processing this directive]
Posted by HeatPro on December 24, 2004 at 07:02:56:
In Reply to: Re: Singular danger posted by tangirl on December 23, 2004 at 21:03:55:
: : You are saying that the boiler goes to 5 psig right away and has to be reset to get the burner going, which means your pressure safety device is not functioning properly.
(I'm assuming that's the box that's set at 1.5 psi?)
: What makes you say it is the pressure safety device?
!!! It is the only control you have that stops the burner. It is set at 1.5 and goes to 5 psig, that is a clue that it is not working right. !!!
: Also, your boiler is steaming very quickly, which can mean the fire has gotten significantly larger from regulator failure or wear.
: Regulator failure - Do you mean a gas regulator or some other regulator?
!!! I mean a gas regulator, as that is the only regulator you have to adjust the gas fire size !!!
Post a Followup