[an error occurred while processing this directive]
Posted by HeatPro on October 29, 2004 at 13:06:13:
In Reply to: oil burner control posted by jonathan on October 29, 2004 at 09:15:20:
Trying to understand an aquastat relay that does not have a number to identify it is pure conjecture.
Assuming it is a good relay that only has the neutral connected together by code, that would indicate a bad connection in your grounding.
Post a Followup