Posted by Leigh on October 18, 2001 at 07:54:00:
We have an ancient boiler that was originally oil converter to gas, it is an American Radiator company boiler (made before the company merged and became American standard) our problem is the pilot is lit, but when the gas kicks on the pilot doesnt ignite the gas to get the burner going. We have to manually light the boiler... We are cold and dont have an appt with our furnace man until next week, is it possible it is simple... The gas releases right near the pilot, so we dont understand why it wont light the burner.
Post a Followup