[an error occurred while processing this directive]
Posted by dave canavarro on September 07, 2008 at 22:36:22:
In Reply to: Re: new Miura Boilers posted by Wayne on September 06, 2008 at 13:36:03:
: We are about to pass one year of operation with our 300hp LX boilers. The only major problem we have had with the boilers, is with the relay board in the control section. We had relays on this board that have discolored, with carbon deposits, and eventually lost enough voltage that they went into some very strange lock outs. What size are yours? You might want to check the soldered relays on the relay boards periodicly for arcing. Water treatment is the key to these babies. Personally I like um. They are cheap to operate!!
Hi Wayne. I agree they are very cheap to operate and water treatment is the key. We installed new water treatment equipement with colormetry just to be safe. We did have some pump contactor chattering but we tracked it down to a loose wire on the water level probe. Wire tightened and problem solved.
Post a Followup