[an error occurred while processing this directive]
Posted by Joe Lambert on July 29, 2004 at 07:43:43:
In Reply to: trap application posted by kraig on July 28, 2004 at 13:25:57:
This is a correct installation. You have a failed trap, could have caused by dirt even through the strainer. Although double check if you have a bypass around the trap that may be leaking.
A disc trap will NOT last long at this pressure. I would recommend a thermostatic trap made by many manufacturers.
Post a Followup