[an error occurred while processing this directive]
Posted by James on March 11, 2004 at 09:45:17:
I am in the process of installing a blowdown heat exchanger with flash tank. Question: Where is the best place to connect the vent piping to the DA Heater? Currently there are no “extra” penetrations installed on the DA that are not in use. Reluctantly, I am considering having a contractor install a flanged pipe connection on the DA (upper section) to accommodate this vent piping. Or should I tie into the low pressure steam augmenting station or consider putting in a “T” on the relief valve or vacuum breaker connections and tying in there? Cochrane has been of little help. So, any information or feedback would be greatly appreciated.
DA is a DS-96
Manufactured by Chicago Heater Company
Post a Followup