Posted by B.T.Bill on November 12, 2001 at 13:36:46:
In Reply to: Deaerator vent spewing water slugs posted by George Larose on November 09, 2001 at 18:38:56:
: At your next available opportunity open up the DA and check the spray nozzles out. One or more of them may have failed wide open or fallen off. If your unit is a Cochrane/Crane also check out the top plate that the nozzles attach to. They have had failures from cracking and erosion. Good luck.
Post a Followup