[an error occurred while processing this directive]
Posted by Peter Hamilton on November 29, 2007 at 17:14:24:
In Reply to: Re: Riello F3 40 series burner posted by HeatPro on November 29, 2007 at 12:52:54:
: If you are providing combustion for a steam system (a reasonable assumption for a steam forum, though not necessarily the fact) then you would total up the radiation output in the building and add 50% to that. If the required btuh of the burner can provide that, it is what you need.
:Thanks for your speedy response, Heat Pro. It's a hot water system. The boiler has T.S.45,000-55,000 stamped on it. Is this any indication of the size? Peter Hamilton http://www.heatpro.us/steamtree/documents/13DCC0F93CE9CBF05551C0B19B792902A9F2BE46.html
Post a Followup