[an error occurred while processing this directive]
Posted by HeatPro on November 23, 2007 at 09:42:48:
In Reply to: Re: Help to replace a Webster Modulation Vent Trap posted by Ken on November 23, 2007 at 07:23:47:
: How do I determine the capacity of the old F&T trap?
Often the pipe size fitting will handle the needed condensate; but make sure by the capacity required from the total radiation and boiler output.
Post a Followup