[an error occurred while processing this directive]
Posted by Victor on November 12, 2007 at 21:24:16:
I have a Burnham hot air furnace. On top of the furnace to the upper left side are the pipes that heat up my basement. Those pipes are running fine and the air temperature in the basement is fine. This compartment composes of 1/4 of the furnace. The other 3/4 area heats the upstairs. The air that's coming out of the register for that side is luke warm. The boiler has a damper that controls the upstairs air flow. How do I adjust the damper? Is there a specific position or way to set the damper to attain maxium heat? Thanks.
Post a Followup