[an error occurred while processing this directive]
Posted by Keith on November 04, 2007 at 15:50:06:
In Reply to: Re: EXPANSION TANK posted by pete on November 04, 2007 at 04:18:58:
I have a New Yorker CG-A Series boiler and i am having the same problem with the relief valve. The only difference is that when I tried to check the psi on the tank there is no air coming out. I have a feeling i have to take off the expansion tank and drain the water but do i have to completely drain the boiler or just turn the gas and water off???
Post a Followup