[an error occurred while processing this directive]
Posted by HeatPro on October 30, 2007 at 12:49:20:
In Reply to: Boiler Constantly Cycling After A Minute or Two posted by Brian Spolarich on October 14, 2007 at 21:21:49:
You've had the electricals tested; however, it could be a water flow problem as well. With the water flow reduced, the boiler can also short-cycle. Check boiler outlet and inlet temperature differences, it shouldn't be greater than 30 degrees.
Post a Followup