[an error occurred while processing this directive]
Posted by HeatPro on October 03, 2007 at 11:03:37:
In Reply to: Worcester combi boiler re-pressurising system problem posted by sam on October 03, 2007 at 10:53:33:
That's an indication that the gauge has gone out of accuracy, or the relief valve has weakened. One or the other or both need replacement.
Post a Followup