[an error occurred while processing this directive]
Posted by Boston on September 27, 2007 at 14:48:45:
In Reply to: Re: Main Vents posted by HeatPro on September 27, 2007 at 12:21:42:
Thanks Heatpro, I apologize, but need a little clarification, my main goes in two directions. The main to the left goes about 2 ft and then Tís off in two directions. One pipe going directly to a 1st floor radiator and the 2nd going to another. Should that short main have a main vent? The other main goes 15ft in the other direction across the basement ceiling and ends with another T and both jet to the second floor. Should I position the main vent 1.5 feet back from that T?
Is the Gurgling caused by trapped air in the main?
Post a Followup