[an error occurred while processing this directive]
Posted by HeatPro on February 04, 2007 at 12:44:56:
In Reply to: t&p posted by joe b on February 04, 2007 at 12:08:09:
The problem is probably that it has a T&P; the relief valve on a boiler is only supposed to be a P. A T&P will dump water regardless of the pressure when the boiler temperature gets high enough.
Post a Followup