[an error occurred while processing this directive]
Posted by Jack Quinn on October 31, 2006 at 16:52:23:
Hello, I have a question about a kickspace heater that I need to install. The heater will be above the run of the line, the inlet and outlets are 1/2 and the main line is 3/4. The manufacturer says that there should be an air bleed installed on the return side of the unit. There does not appear to be enough height to install an auto-vent since it would hit the bottom of the cabinet. Is there another type of bleeder that can be used? I tried to have this installed, but nobody seems to want to do it. The original plumber I had left the heater and never came back.... any help would be very much appreciated!
Post a Followup