[an error occurred while processing this directive]
Posted by HeatPro on June 17, 2006 at 14:04:06:
In Reply to: Re: Circulator location? posted by joe on June 17, 2006 at 12:18:31:
If you are using a tube-type boiler that has a significant pressure drop, yes. Doing so will allow the pressure-drop through the boiler to be from a higher fill-pressure start than if pumping away from the boiler.
The primary-loop drawing in the article about preventing sizzling would have little difference when pumping-away from the expansion tank on either side of the boiler unless the boiler has some significant flow resistance due to small tubing.
Post a Followup