[an error occurred while processing this directive]
Posted by HeatPro on April 29, 2006 at 23:18:44:
In Reply to: Re: 2 Stats - 1 relay - 2 pumps posted by Jeff on April 29, 2006 at 01:16:50:
: This is a Honeywell Aquastat Relay L8048F. Could this relay actually handle the pumps independantly?
+ No, this control is not a multi-zone controller.
You need another R8445 relay to control the other zone and wired as a second zone to fire the boiler from the 8048.
The two stats can be wired, without good purpose to the T and TV, as stats are just switches.
Post a Followup