[an error occurred while processing this directive]
Posted by Dave on March 15, 2004 at 16:02:00:
In Reply to: Re: what is going on with my system posted by Dave on March 15, 2004 at 11:34:29:
I was told by the guy from the gas company that came to replace the cartridge today that the minimum flow for the boiler is 12gpm, and the head is around 5-10. He said the 0012 is moving way too much water. He said that we should have a pump that moves about 20-25 gpm and recommended a Taco 0010. Does this sound correct?
Does the 0010 come with flanges for the 2" piping in the primary circuit?
Post a Followup