[an error occurred while processing this directive]
Posted by jtown on March 04, 2004 at 05:34:42:
In Reply to: END OF HEATING SEASON posted by bill hallman on March 03, 2004 at 01:26:13:
Do regular monthly. Blowdown boiler and fittings. If adding water, run it for an hour or two to remove Oxygen from water. Shut off any make-up line and shut off electric so it doesn't get fired by someone nudging the stat. A higher or lower waterline might add some life as corrosion can occur right above the waterline, where water air and iron meet.
Post a Followup