[an error occurred while processing this directive]
Posted by Dave on January 22, 2006 at 08:38:11:
In Reply to: Re: The plot thickens... posted by HeatPro on January 21, 2006 at 11:23:05:
Thank you very much. I was misunderstanding when you were saying high limit. I thought you met the dial that we set for the highest temp that the water will be. You are referring to the actual safety limit device that is in the outflow section of the heat exchanger. I disconnected ours and there is no alarm ,and the pump does continue to run, so it should be fine. As far as the gray wire that the Heatmanager people show for the 24v, is that necessary for my situation? If so, where is that best to tap off of?
Post a Followup