[an error occurred while processing this directive]
Posted by Joe Brix on January 07, 2006 at 08:50:16:
In Reply to: To Joe Brix posted by Bill on January 06, 2006 at 18:55:57:
Heatpro answer the question: There's none to adjust on a CGi. While you're doing the piping work, you might want to think about an outdoor reset control like the Tekmar 256 (or 260 if you're heating an indirect HWH). The outdoor reset will run the boiler to a lower temp when it's warmer out and allow you to set a wider temp differential before csalling for the gas valve to fire. You'll need a temp sensor well installed in the supply piping.
Post a Followup