[an error occurred while processing this directive]
Posted by jtown on November 18, 2003 at 17:39:36:
In Reply to: Not Enough Heat posted by Tom on November 18, 2003 at 09:54:50:
Lower pressure to minimum. look for sagging in piping to rear in basement, including "swing arms" or angles made by piping to allow expansion. Water in low spots will limit steaming. Switch air vents with some on front.
Post a Followup