[an error occurred while processing this directive]
Posted by Heatpro on December 07, 2005 at 15:39:34:
In Reply to: "Double" Clicking-relay posted by Pete on December 07, 2005 at 15:17:37:
The right-left wiring of the end switches is nothing. There are simple switches between the right and left end switch terminals, bi-directional, so no problem about that. If it will annoy you, just swap the wires on the zone 1 end switch teminals so they are all the same.
You probably have a dirty microswitch contact or maladjustment of the bump that moves the switch in the zone 1 valve, so you could change it or leave it til it doesn't work with or without a double click.
Not a big thing to worry about.
Post a Followup