[an error occurred while processing this directive]
Posted by Heatpro on November 23, 2005 at 14:06:37:
In Reply to: cut in settings posted by jim on November 23, 2005 at 12:27:42:
As steam will go up 2/3rd of a mile at 1psig, ounces is all you need. REsidential steam systems were designed for 1 psig, so the lowest you can set it so it operates and goes on and off dependably is the number. Steam radiator vents go bad over 3 psig, so keeping it low is a benefit.
Post a Followup