[an error occurred while processing this directive]
Posted by Mike on October 11, 2005 at 21:57:59:
In Reply to: Wiring a Mectron 3m posted by Darren on October 10, 2005 at 11:55:52:
: I purchased this unit complete and have been unable to find any information on wiring it. The guy I bought it from has since moved and I cannot find anyone who is familiar with it, can anyone help me to figure out which terminals are which...I'd hate to wire it wrong.
The Mectron is better known as a Riello 40 series Burner, Models F3 and F5. I know you have an L Terminal that takes the hot side of the 120V and then the neutral side gets the N terminal and also connect an earth ground. The power head has all the connections needed internally but you'll need a switching relay controlled by a low voltage stat like the R8038A by Honeywell,...no matter what, get the manual it has alot of info you will need to set it up correctly.
Post a Followup