[an error occurred while processing this directive]
Posted by george on January 19, 2004 at 17:52:42:
I have an old Axeman steam furnace and The
LARGE pressure gauge on the top has many
positive and I guess, negative numbers,
The meter is always at -3 when steam is
running or the furnace is cold. I know the
pressure should be about 1psi and the hi cut
off next to the meter is set the lowest setting.
I assume the gauge has seen its beter days.
What meter should I replace it with?
It seems like a simple pipe wrench task.
Post a Followup