[an error occurred while processing this directive]
Posted by dave_in_brooklyn on January 12, 2004 at 16:24:26:
In Reply to: Re: cut-in limit reached... posted by Harold hydronicnetwork.net on January 12, 2004 at 07:46:39:
: Sediments in the siphon loop below the pressure switch and in the pressure switch could have something to do with it. Switches get old and stray.
: Sediments in the condensate line would have more to do with low water problems.
**Turns out that the "Pig tail" connected to the "cut in" mechanism was completely clogged up with dried sluge.
I replaced it ($4.25), and I now have heat with a much lower cut in.
Post a Followup