[an error occurred while processing this directive]
Posted by Ralph Blaine on January 11, 2004 at 15:00:09:
In Reply to: Re: Problem radiator posted by Harold hydronicnetwork.net on January 11, 2004 at 13:27:38:
: Suspect a line pitch problem that is acting as a trap for the condensate. Also, test the main vent by adding a small vacuum breaker on the vent hole with a tee with the vent on the problem radiator. Some adapters would be needed to make up the little manifold. This could be done manually by waiting for the steam cycle to end and then removing the vent to see if water falls out faster. The vacuum breaker would allow the water to fall from the radiator against some resistance below.
Post a Followup