[an error occurred while processing this directive]
Posted by Harold hydronicnetwork.net on January 09, 2004 at 18:51:26:
In Reply to: constantly filling my Bryant gas fired steam boiler posted by Tom on January 09, 2004 at 17:34:08:
Yes, vents on steam radiators that hiss all the time are mot shutting down when the steam hits them, so they are steam-cleaning the house. Make sure the steam pressure does not go over 2-1/2 psig, or the steam vents are damaged. Replace the hissing steam vents with new ones that will stop hissing when the radiator is filled with steam.
Post a Followup