[an error occurred while processing this directive]
Posted by Jeff on March 14, 2005 at 14:49:16:
In Reply to: Burnham Boier nosie posted by steve h2 on March 11, 2005 at 19:09:56:
: I have a 11 year old Burnham boiler (oil/steam) and when it starts up to heat it sounds fine. When it shuts off, it rumbles, noticeably enough that the house seems to tremble a little. Some times it happens every 10-20 minutes and then repeats itself. I know its cold out but this has been happenning for a week now. Does anyone know what causes this shut down rumble? Thank you.
: steve H2
Sounds like an afterburn problem. Could be loose nozzle, bad fuel pump cutoff, air bubble in nozzle line etc. Your gonna need a tech for this one as special tools will be required to diagnose it.
Post a Followup