[an error occurred while processing this directive]
Posted by HeatPro on February 11, 2005 at 19:06:02:
In Reply to: Weil McClean GV 5 Blower Rapid Start / Stop posted by David Hillman on February 07, 2005 at 11:48:41:
Have a service person with an inclined manometer or magnehelic gauge check the gas pressure and examine and clean the flame sensor. It is probably cycling while trying to establish a proper flame.
Post a Followup