[an error occurred while processing this directive]
Posted by Glenn on September 02, 2004 at 07:12:47:
In Reply to: Re: Residential Combination Gas/Oil Boiler posted by HeatPro on September 01, 2004 at 18:20:22:
: For a somewhat poorly insulated houue of 5000 square feet, a combination boiler for heat loads over 220,000 btuh can be handled by a combination burner.
: A choice can be made between using a combination burner or two separate burners for gas and oil, as the switching requires burner combustion testing to assure clean combustion.
Thanks for your feedback. I don't quite understand re the combo or separate burners. Is it that 2 separate burners don't require combustion testing and that's why you should go for the 2 separate ones? glenn
Post a Followup