[an error occurred while processing this directive]
Posted by jtown on May 18, 2004 at 05:45:32:
In Reply to: To Big To small posted by LowBottom on May 16, 2004 at 07:31:25:
Hopefully, you have valves that allow throttling the warmer rooms a little bit, waiting a day and repeating. Look for how the water travels. If it indeed goes through one then the next, you cannot throttle it, and have to balance the radiators to each room and the amount of heat to the circuit must be sufficient (flow and temp). You might block air flow at the bottom of the warmer room's radiators. Separating the bedrooms as another zone could help if the piping is too small. Then you could run them cooler.
Post a Followup