Posted by Billy on November 13, 2001 at 17:53:05:
In Reply to: Re: Help; stam boiler low level cutoff posted by Harold Kestenholz - Hydronic Network on October 22, 2000 at 13:43:10:
: This system is operating as if it has no Hartford Loop to keep the water level in the boiler constant. Also the pressure may be set too high, there is oil or dirt on the water, or the boiler does not have enough water content to steam until condensate returns to the boiler.
Post a Followup