Posted by max on January 08, 2000 at 16:11:04:
this is the reading on my American Standard boiler with White Rogers regulator, with a grey 3x3x6 box with 105 reading on it, forgive me if I use the wrong termenalogy.
I've just pull on a spring loaded valve below the grey box, and I heard the water moving for 10 sec. and stopped. I waited for the water to be heated more, and pull the valve, it ran for another 10 sec. and started dripping down from the plpe.
I've checked the radiator, and it still have negative pressure. Shall I bleed the radiator, at least let in some air and balanced out the pressure? What shall I do next?
Post a Followup