[an error occurred while processing this directive]
Posted by Sunny on August 21, 2003 at 01:24:37:
1. For performance test for my co-generation plant, one of the parameter I should know is the enthalpy of exhaust of gas turbine that goes into the boiler. Is there any standard to calculate that figure because I couldn't find any.
2. What about the H2O %volume in the exhaust gas? Do I have to solve the complicated combustion equation for natural gas? Or, do we have to measure straight forward at the stack? Please help.
Post a Followup