[an error occurred while processing this directive]
Posted by PP Steam on February 12, 2007 at 15:30:28:
In Reply to: condesate posted by Ed on February 06, 2007 at 11:27:19:
The best thing to do is flash the condensate to a lower pressure steam header. It may take a couple of stages but you should be able to flash it down to around the same temperature as you deaerator. YOu would not want to pipe high pressure condensate directly to your deaerator as it would flash, possible hammering lines, and potentially losing some of its energy out the DA vent.
: Where is the best place to send condesate from the steam header,currently it is going to the drain.
Post a Followup