[an error occurred while processing this directive]
Posted by Rick on December 17, 2006 at 20:36:52:
In Reply to: Bouncing water and cyclohexylamine posted by Robert Kemp on December 15, 2006 at 15:48:43:
: We have a sectional cast iron boiler and have trouble with water carry over and bouncing water level. This seems worse a few hours after we add cyclohexylamine to the return lines. Does anyone have experience with this and if so, is there a better additive? Our pressure is 10PSIG.
The cyclohexamine should be fed directly to the steam header not to the condensate return lines.
Post a Followup