[an error occurred while processing this directive]
Posted by Art Parent on November 14, 2006 at 16:02:25:
In Reply to: H.B.Smith 450 A posted by JR on September 14, 2006 at 10:25:50:
: I have questions about flue damper adjustment , our boilers have actuators to open and close dampers but they not hooked up. I have adjusted them to gain the best draft cold , But I think they should modulate depending on load ? Dose any body know the correct opperation ? Thanks
Reply to outlet dampers:
actuator should be controlled by a sequencing draft controller. Overfire draft is critical to efficient combustion and ever dependent on countless variables such as firing rate, fuel, ambient temp., outside air temp., etc., etc., etc.
Post a Followup