[an error occurred while processing this directive]
Posted by Bob D. on May 03, 2006 at 10:40:15:
In Reply to: insulation for condensate tank. posted by robert on May 03, 2006 at 04:10:11:
Owens Corning Pipe & Tank Insulation, or equal. Fiberglass, segmented, all-service jacket (ASJ), thickness to suit local Code, insurance, or economic payback criteria requirements. You could also do AL or SS jacketing depending on your requirements. This is pretty routine. Just be sure your gage glasses and instrument wells extend far enough, and use removable "jackets" at manholes, etc.
Post a Followup