[an error occurred while processing this directive]
Posted by tmiller on October 30, 2005 at 08:52:57:
In Reply to: deaerator posted by afdmello on October 29, 2005 at 07:03:54:
Could be the vent valve is not open far enough. A properly vented DA should have a 3 to 5 foot plume from the vent pipe. Many DA vent valves have a 3/8" hole drilled in, and in order to avoid visibility problems the valve ends up being shut, and the 3/8" hole relied on for venting, causing condensation in the vent pipe. Determine the proper valve opening by testing for dissolved oxygen, then leave it in that position.
: what are the causes for water ejecting from the deaerator dome vent along with steam vapor.
Post a Followup