[an error occurred while processing this directive]
Posted by C S on November 24, 2010 at 17:43:52:
In Reply to: Re: clayton steam generator posted by C S on November 24, 2010 at 17:36:09:
: : Having some issues with low pressure output from feedwater pump, and primary trap off of separator staying open. Trap was opening and closing fine untill fire rate got torwards the high end then it opend up...guage off of trap line reads 25psi and trap stays open..any ideas?
Check your gas pressure and cubic feet per hour of gas or gallons per hr of oil. You might not have enough heat to vaporize the water at high fire. I like to see the trap discharging tw0 to four times a minute, that way you are producing dry steam.
Post a Followup