[an error occurred while processing this directive]
Posted by Damon on June 10, 2010 at 14:26:30:
In Reply to: Re: Cleaver Brooks Water probe Issues posted by David Stewart on June 09, 2010 at 14:00:35:
What are you use caustic on the boiler itself for? Do you have a R.O. system? If so I would suggest do what we did. We have the caustic injecting into our condensate tank that what it helps treat that tank, the DA and the boilers. Plus this way you don't have to consentrated caustic going into the boiler. Let me know what you get on the chemical test near the water columns.
Post a Followup