[an error occurred while processing this directive]
Posted by sid on April 01, 2006 at 21:49:47:
In Reply to: Cleaver Brooks CBLE posted by Jared on March 28, 2006 at 22:55:55:
Could be you modulation motor is in manual no atuomatic or a bad modulation temperature control.
check to make sure you are in auto. try the temperature control off the other boiler . If you payed C/B to come out i sure hope they give you a hat and coffee cup >>
Post a Followup